Tata & Howard completed a hydraulic model update and Capital Efficiency Plan™ for the City of Worcester. As part of the project, Tata & Howard updated and verified the City’s existing hydraulic model, which has over 550 miles of water main. Work included three days of fire flow tests throughout the City and allocation of demands using up-to-date billing and parcel data. Phase II of the project, the Capital Efficiency Plan™, identified and prioritized areas for improvement within the distribution system. Our services included evaluating the condition of the existing distribution system infrastructure to determine the adequacy of meeting present and future demands, calculating needed storage requirements, assessing and prioritizing system improvements, reviewing and evaluating typical fire flows throughout the system, creating a pipe asset management rating system, and recommending improvements to the distribution system.
Tata & Howard calibrated the hydraulic model under extended period simulation for an evaluation of the Super High Service Area with the Chester Street Tank off-line due to rehabilitation. The configuration of the service area included two distinct zones. The Chester Street Tank is located in one area and the Howland Hill and Apricot Tanks are located in the other area. To remove the Chester Street Tank from service, an evaluation of supply and pressures needed to be completed. The results of the analysis included running both zones off the Apricot Tank and utilizing the Chester Street Pump Station to maintain pressures within the vicinity of the Chester Street Tank.