Water Distribution System Evaluation and Tank Design, Paxton, MA
Town of Paxton, MA
Tata & Howard provided engineering services for a comprehensive water distribution system evaluation and study. The work included development of a hydraulic model using WaterCad software. The plan included fire flow tests, review of the water supply agreement with the City of Worcester, preparation of projected water demands based on historical use and population trends, and evaluation of storage. The plan also included an evaluation of potential water supply sources within Town boundaries.
This project included an evaluation of the system prior to design of the tank to determine the best solution. Work included calibrating the model under extended period simulation (EPS). The hydraulic model was used to determine the best hydraulic gradeline elevation of the system to reduce the storage surplus. Additionally, the model was used to track the chlorine residual from the Worcester Pump Station to the extremities. Jar testing was completed to determine the chlorine demand in the water supply while water quality testing results assisted with determining the chlorine demand in the piping system. The model was used to simulate the chlorine degradation. Improvements were input into the hydraulic model and the effects on the chlorine residual in the extremities reported. Improvements such as an elevated tank at Maple Street with a total usable volume, reduction in hydraulic gradeline elevation, and cleaning and lining water mains were evaluated. The analysis determined that a new tank at Maple Street is necessary based on water quality and cost.
Tata & Howard provided assistance with the preparation and submittal of a Project Evaluation Form to the Massachusetts Department of Environmental Protection for the construction of a new elevated tank with a capacity of 0.2 million gallons. The new tank reduced the water age in the system by replacing the deteriorating ground level tank. Tata & Howard provided construction administration and resident observation services for the new tank, which was completed in 2016.
ABSTRACT: In 2012, the Town of Paxton, MA was experiencing significantly reduced chlorine residuals in the extremities of the system along with an aging water tank that required extensive rehabilitation. As a result, the Paxton Department of Public Works (DPW) determined the need to create an extended period simulation (EPS) hydraulic model to evaluate the water age and water quality in the distribution system. The study examined the residual chlorine concentrations and water age throughout the distribution system and presented various options to help mitigate these issues, including replacing the aging tank and adding a chlorine booster pump station at the existing site. Construction of the new tank and pump station was completed in the summer of 2016. Read the complete whitepaper by clicking below:
To download “Town of Paxton, Massachusetts Distribution System Evaluation and Improvements” whitepaper instantly, simply fill out the form below: