The wastewater treatment plant in Lyndon, Vermont was experiencing excessive odor issues. The existing odor control system relied primarily on chemical treatment, which was difficult for the operators to manage. Tata & Howard’s project design consisted of a bio-filter with root mulch to remove the odors, which are primarily ammonia, that are generated from the Auto Thermophilic Aerobic Digestion (ATAD) sludge treatment vessels. The ATAD system is a system that results in class A sludge that can be spread anywhere as a fertilizer, and it reduced the annual volume of sludge produced at this facility by 65%. The new system includes fans that pull the air off the top of the ATAD unit vessels through a cool down water wash tank, which knocks down the ammonia, and then pushes the air through PVC piping up through the root bio-filter shown in the picture. The total cost was under $300,000, for which Tata & Howard procured the Town a 100% grant.
The second part of the design project included a nitrogen reduction system for the secondary aeration process that may be necessary in the near future. The design includes a recirculation pump system from the Anoxic zone back to the Oxic zone. The Contractor was T. Buck Construction of Maine.